Tunnel Furnace Test
|Flame spread value 0
Smoke density factor 0
Fuel contribute 0
Test extended to 30 minutes
Hardwood Plywood Manufacturers Association Tested in P .0. BOX 2789
2 hr Test
ASTM E814 / UL 1479
CT State Building Inspector
New York City MEA 68-91-M
|The initial ambient temperature was 57°F.
Hose Stream Test: No holes formed in the unexposed side of the
sample after being exposed to the hose stream for 24 seconds.
F Rating: 120 minutes
The sample met the acceptance criteria of the "F Rating" for 120
Minutes per ASTM E814/UL 1479 specifications.
|3||Formaldehyde & VOC Test||
|The emissions test results indicate that neither formaldehyde nor volatile organic compounds are emitted from the airKrete insulation at 24 hours and 96 hours from manufacture.|
|4||Mold Growth Test||ASTM Guideline D 6329-98||
Results show that the AirKrete Insulation Sample was resistant to mold growth at both 75% and 95% relative humidities. Neither molds were found to amplify in the materials at either humidity.
Air Quality Sciences
|5||Shrinkage Test||ASTM C951||No Shrinking - After spraying 40 days at 75% and 50% relative humidity||
Twin City Testing
|6||Sound Test||ASTM E90||For any pair of rooms and microphone system, the 95% confidence interval TL, for transmission
loss must be less than the following.
Range of Transmission Loss
One-Third Octave Uncertainty, dB
Bands Required Actual
125 and 160 3 <1.5
200 and 250 2 <1.5
315 - 4000 1 <1
|7||Thermal Conductivity Test||Thermal Conductivity||
|8||Water Permeability Test||ASTM E96 / E96M - 10||0.3701cm/S Standard Test Methods for Water Vapor Transmission of Materials|